CEU: NEC Changes Class in Northglenn
Date(s) – Saturday, February 9, 2019
8:00 am – 4:30 pm
IECRM Main Campus
About this Class
This is a Saturday 8-hour CEU that will help you understand the newest changes to the 2017 NEC Code.
The National Fire Protection Association (NFPA) publishes an updated version of the NEC® every three years. After incorporating the efforts of the general public and more than 300 volunteer members of code-making panels, the 2017 edition has been released for adoption into local statutes by governmental bodies that have legal jurisdiction over electrical installations.
Article 425, titled Fixed Resistance and Electrode Industrial Process Heating Equipment, provides installation rules for industrial heating equipment not addressed elsewhere in the code.
Article 690 provides installation rules for Large-Scale Photovoltaic (PV) Electrical Power Supply Stations. These systems are privately owned and no smaller than 5000 kW in size.
Article 706, Energy Storage Systems (ESS), accommodates those systems that are intended for short term augmentation of the utility supply during peak consumption times.
Article 710, Stand-Alone Systems, is a small article that addresses any small alternative energy supply systems such as wind machines, photovoltaic systems, or others where other NEC® articles are not sufficient to provide the necessary installation rules.
Article 712, provides for small direct current systems that are being used where security from outside threats are a concern. This new article ensures the systems will provide reliable and safe service in a critical function.
New and Clarified Rules
In addition to the new articles, the 2017 NEC® provides clarification to existing rules as well as new rules that will reduce the risk of fire or electrical hazard exposure to workers. Following are some of the key changes [citations in brackets]:
An arc flash warning label that contains detailed information about the electrical system must now be attached to service equipment to inform workers of potential arc flash hazards. [110.16(B)]
Reconditioned electrical equipment must be marked with information about the reconditioning manufacturer as well as performance data to certify quality. [110.21(A)(2)]
Working space for the protection of a worker providing service or maintenance is defined for electrical equipment operating between 601 volts and 1000 volts, and for equipment located in limited areas such as above dropped ceilings. [110.26(A)(4) and Table 110.26(A)(1)]
The distance from a sink to a location where an installed receptacle must have Ground Fault Circuit Interrupter protection is clarified to not include those located under the sink. [210.8]
The use of Arc Fault Circuit Interrupter protection has been expanded to reduce the risk of fire in dwelling units. [210.12(B)]
Meeting rooms now will have a minimum number of receptacles to limit the use of extension cords. [210.71]
The temperature adder to correction factors for conductors installed on the roof is removed so long as the raceway is installed at least 7/8” above the roof surface. [310.15(B)(3)(c)]
The rule prohibiting flexible cords above a dropped ceiling has been relaxed for equipment that is listed for environmental air spaces, permitting some projectors mounted on the ceiling to be fed from above the dropped ceiling. [400.12(5) Exception]
Tamper resistant receptacle rules have expanded to more areas and configuration of receptacles where children may have access. [406.12]
The ground fault trip threshold has been reduced for circuits supplying marinas and boat docks in response to recent electrocutions occurring at those locations. [555.3]
There are new rules that require a rapid shutdown of photovoltaic systems to protect the emergency response personnel such as fire fighters from the electrical hazards associated with those energized systems. [690.12]
And many more…
NOTE: All purchased book(s) will be distributed on the first day of class!
Register below or view all upcoming CEUs.
NOTE: All purchased book(s) will be distributed on the first day of class.
- OPTIONAL: 2017 NEC Code Book
- OPTIONAL: 2017 NEC Changes Book
- OPTIONAL: Optional TABS for Code Book
2017 NEC Code and other optional items are now available! Get yours at iecrm.org/books.
Please Note: This CEU class meets the new Colorado state requirements for the 2017-2020 code cycle. See below for more information from DORA’s website.
New Continuing Education Requirements for Colorado Electricians
Governor Hickenlooper signed House Bill 16-1073 into law on April 15, 2016. This law replaces the current continued competency program with a requirement of 24 hours of continuing education to be completed each renewal period. The Continuing Competency (CC) Assessment will no longer be administered.
Before renewing your license in September 2020, all licensed electricians will have to complete 24 hours of continuing education, called Continuing Education Units (CEU).